|Min. Order:||1 Bag/Bags|
Generator Type: Alternator
Output Type: AC Three Phase
Certification: CE, ISO
Packaging: In cases
Port: Qingdao Port
Steam Turbine Generator Care
Trust QNP`s knowledge and experience in steam turbine inspection, assessment and service.
QNP Maintenance and Installation Engineering Co., Ltd. is QNP`s subsidiary company, and has power engineering construction qualification.
350MW generator maintenance 350MW generator maintenance
I. Generator grid-connected without synchronization
Before grid-connected, the voltage, frequency, phase sequence and phase position of generator should be in step with grid. But under some conditions, the client doesn`t check phase or synchronization device fault when grid connected. It causes grid-connected without synchronization and it damages generator and power systems. The generator stator will be attacked by a huge electric current under grid-connected without synchronization. The current meter will swing violently and the voltage meter will swing also.
The huge current will severe impact on generators, transformers and the system. The STG will shake strongly and make the generator winding deformation, twisted, insulation cracked and make the end to end joint sleeve of windings melt. It will cause some serious hidden dangers even burn windings. For the whole power system, if a big STG connect to the grid without synchronization, the power shock will happen between the generator and system. It will disrupt the whole system operation normally and even make the entire power system collapse.
This is a generator of Inner Mongolian client. The non synchronization accident occurred when the generator was on automatic synchronization. It made many tying torn apart and more than two thirds of coils insulation cracked and B-phase grounded.
When we repaired the generator, we removed all coils and made withstand voltage test for those coils. For the non-destructive coils, we used them after cleaned up. For the failed coils in test, we treated them with re-insulation re-offline, testing, welding ends and completed factory withstand voltage test. When we inspected the relay protection system, we found the synchronization screen fault in grounding. After adjustment return circuit of synchronization and accomplishing simulate synchronization, we make the generator connected to the grid successfully.
II. Generator short circuit, insulation breakdown
The insulation breakdown accident often occurred in generator. It includes interphases short circuit, inter-turn short circuit and ground fault.
The interphase short circuit: the generator windings ends will be greatly impacted by electric power and may make the coil end deformed under two-phase or three-phase short circuit and differential protection tripping happening.
Inter-turn short circuit: Generator outlet blasting, if it continues a long time, the stator copper wire will be melted. When no-load run, the generator three-phase voltage will be imbalance.
Ground fault: Generator breakdown location is in the linear portion or notch position and stator ground protection act. The insulation resistance value between stator ground and ground is zero or minimum.
The fundamental reason of generator insulation breakdown is that the stator coil insulation is weak or there is a corona etching in notch in run time. The treatment method is to find the point of breakdown and reworked and reinforced insulation. At the same time, eliminating the corona etching in a maximum extent is important.
III. A large noise or vibration with generator
The reasons of a large noise or vibration with generator are:
1. Foundation bolts loose, or STG subsidence. Treatment: fastening bolts. Recalibration concentricity.
2. Generator rotor and steam turbine shaft are misalignment. Treatment: calibration concentricity.
3. Bearing wall worn or damaged under short oil. Treatment: repaired bearing or replace a new bearing with same model.
4. There is a friction between the stator and rotor. Treatment: find the friction location and reason, and then eliminate it.
5. Fan or other fasteners loose. Treatment: Tighten fan and fasteners.
6. Rotor coil partial short circuit, two points grounding or wiring errors. Treatment: please inspect the insulation of slip ring and the rotor coil to the ground. Or connect to the DC power source and check the voltage drop of each coil, winding direction and wiring method. So we can identify the cause of the malfunction and eliminate them.
7. Brush is too hard, or the pressure is too large. Treatment: adjust the pressure or replace the same type of brush.
8. Three-phase current are severe asymmetry. Treatment: please investigate that the three-phase current imbalance is in the allowable range or not. If it is not in the allowable range, please adjust three-phase load or reduce the load.
9. Stator winding short circuit or ground. Treatment: Find out the fault and repair it.
10. External fault or lightning strike. Treatment: if the vibration time is too long, please stop the STG and inspect.
50MW Steam Turbine Generator Rotor Maintenance
This is a 15 MW generator from a Shandong customer. The vibration of generator is reached to 0.12mm in running. After inspection the generator, we found that rotor dynamic AC impedance upheaval 12% in 2400-2700 and the dynamic inter-turn short circuit is serious. It destroys the balance of the magnetic field and causes the electromagnetic force uneven of generator rotor. After removal of the rotor retaining ring and treatment the rotor inter-turns, we start the STG. The vibration is about 0.01mm.
IV. The temperature of a generator is too high.
Generally the temperature of a generator will be in the allowable value, if the generator running normally and the current, voltage, frequency, power, excitation current and power factor are all within the allowable fluctuation range. If a generator stator, core and other parts temperature are too high, please consider the following cases:
1. Generator overload operation and exceed the allowable time. Treatment: Please reduce the generator load to the rated load or under rated load as soon as possible.
2. Three-phase current are serious imbalance. Treatment: please find out the reason of imbalance. If it is the voltage causing, please check if it is the generator inter-turn short circuit. If it is load causing, please adjust the load and make it balance.
3. The ventilation cooling system of generator is poor. For example, the temperature is too high, the air duct or exhaust duct are blocked, the coil and its ends are serious fouling. Treatment: please reduce the load suitability, improve ventilation, and remove fouling.
4. The stator winding portion short circuit or ground. Treatment: Find out the short circuit or ground point and repair them, and then eliminate short circuit or ground risks.
5. Insulation of the stator core may be partially damaged and short circuit, so there is a vortex and overheat. Treatment: please reduce the load suitability. If the generator reduces its efficiency obviously, please repair the generator stator core.
6. The bearing is short of lubricating oil. The oil number is wrong. The oil quality is bad. The bearing is installed with a wrong way or the bearing is damaged. Treatment: please find out the reason and then replace the oil or clean, adjust or replace bearing.
V. Generator rotor ground
Symptom: Generator grounding one point or two points grounding light plate light.
Fault Analysis: Generator rotor winding insulation damage, coil deformity and severe dust and greasy attached in the ends seriously are all leading to the grounding of the generator rotor windings. When the generator rotor winding grounding in one point, there is electrical current pass as the ground does not constitute an electrical circuit.
However, after one point grounded, it is easy of leading another grounding point. If any part in excitation circuit ground, it can form ground fault of two or more points ground. It is very dangerous.
After the failure, the rotor windings are short-circuited. Because of the small winding DC resistance, the excitation current will increase. So the magnetic field of generator is out of balance, and main magnetic flux reduces largely. So the STG will vibrant strongly. Meanwhile the power factor of the generator will be increased significantly and get into leading phase running (absorption of reactive power from the grid).
The stator field becomes in the frond and the rotor field becomes in the back. It will make the stator current increases. If the watcher notice that there is no excitation varying but the excitation current and stator current suddenly increases, and the excitation voltage and AC voltage are all suddenly drop, and power factor meter indicates increasing or leading phase, it means the generator rotor grounded or inter-turn short circuited. You should shut down the STG and blow-out magnetic. Please inspect the excitation system and rotor windings, and find out the short circuit point and treat it.
VI. Excitation upgrading and generator test
Excitation system upgrading, brushless exciter changes into the SCR excitation and make the generator maintenance easily. And it removes the disadvantage of brushless excitation dynamic adjustment slowly. The generator test includes stator insulation resistance test, the absorption ratio test, the iron loss test, leak test, AC and DC voltage withstand test, the rotor high speed balancing and overspeed test, dynamic and static AC impedance test, the generator no-load test, short circuit test, temperature rise test, residual pressure measurement, axis voltage measurement.